Pipe A looks like a vertical leg for a wet vented toilet, not a soil stack. If so your maximum accumulated change of direction on the horizontal pipe b is 225 degrees.BoatyMcBoatface wrote: ↑Nov 3rd, 2017 1:32 pmThanks to miscommunication and a general failure of common sense, I need to move the soil stack (A) away from the wall another 4"
I don't want to cut back any further than necessary, so is there any code that says I can't put an elbow (Probably a 22.5) on section B which will shift the bottom out to where it needs to be. My concern is anything relating to the number of elbows before it hits the main down stack?
If it is a soil stack there is no limit so long as it’s sloped properly and no horizontal 90s are used