WikkiWikki wrote: ↑Oct 8th, 2019 1:41 pmDo you get flame in the burners. If not, depends on your igniter, it could be gone. If it goes through the stages of it and the igniter is gone. NG wont flow either.
Glow igniters can be replaced yourself and cant be cleaned or repaired. if the filament inside (like an old school lightbuilb) is broken, it wont work.
Also check, the door switch for the furnace fan location. Ive seen those get flaky, and it will let the fan run, but be some odd non connection the furnace wont run. Ive had it happen to me. I could hold the switch down with my thumb, and the furnace ran fine. As soon as I put the door on, the furnace would not fire, but the fan would work
Thanks. After some poking around and a lot of YouTube, I figured out that the draft inducer motor wasn't spinning. I hand turned it a bit (and I mean a tiny bit) with the power off and that seems to have done the trick. It works properly now. I'm guessing there was some gunk or corrosion that was blocking it.
Upon further inspection, I noticed that when I hand turn it very slowly I can hear a light clinking noise when it hits a certain spot. When I spin it faster, I don't hear anything. Does it need to be changed now or can I wait a bit?
(='.'=) This is Bunny. Copy and paste bunny into your
(")_(") signature to help him gain world domination.